Neutral Earthing (Grounding) Reactors, which resist current flow through inductive elements, are single phase reactors generally connected between ground and neutral of transformers or generators in order to control single line-to-ground faults at a desired level.
Neutral Grounding Reactors are used in order to limit line-to-ground fault current to a value which will not damage the equipment in the power system, yet allow sufficient flow of fault current to operate protective relays to clear the fault. If the circuit is balanced, current flow through the reactor will be zero, thus, there will be no losses.
Neutral Grounding Reactors reduce short circuit stresses on station transformers for the most widespread type of fault in an electrical system.
A loaded generator can develop a third-harmonic voltage. Providing impedance in the grounding path by Neutral Earthing Reactor, can limit the third-harmonic current.
Area of Usage
- Reducing single phase to earth fault currents which occur in electrical networks to prevent damages on transformers and generators
- Reducing temporary over voltages formed by braking instantaneous fault current
- Providing long-life for switchgear
- Reducing step voltages to a harmless level for personel
- Perfect mechanical strength to withstand high short-circuit forces
- Limited temperature rise enables longer lifetime
- Special surface protection against UV and pollution Class IV areas
- Maintenance-free design
- Low noise levels