Primary Current Injection Tester is designed for testing protective relay and circuit breakers and also testing the turns ratio of current transformers at high variable currents.
A test current is injected into the primary side of a system to determine how the system behaves at particular levels of current. This test makes it possible to determine whether the relay will trip and how long the current needs to flow before the trip is initiated.
Independent loading scenarios on each phase can be applied.
Area of Usage
- Three phase primary current injection
- Testing of protection relays
- Thermal and magnetic device testing
- Temperature rise test and trip test of circuit breakers and junction points
Depending on the test to be performed, turn the position switch to the proper selection (example : 3x2.5 V 4000 A or 3x400 V 45 A). Install the intermediate connections with minimum 2A/mm2 current density cables which have equal cross-sections and equal length. If any gap is left between current carrying cables, because of the effect of inductance, maximum current can not be reached. The best solution is to have a touch between current carrying cables. Thermometer probes must be connected to the measurement points with tongs or tapes.